LED Lights SPDs
Surge Protectors for LED lighting system
Nevertheless this attractive technology has an important weakness: its sensitivity to transient voltages created by lightning or by power switch operations on AC network.
Due to its scattered and over-exposed location, LED lighting system will face induced surges which will create failure of its power supply, damage LED components or loss of the lighting efficiency. For these reasons, the use of relevant surge protectors located upstream the LED lighting systems is highly recommended.
LSP offers a surge protectors designed to be installed at different points on the lighting network such as streetlights, the base of poles and street cabinets.
The DSLP is a compact solution surge protectors to be installed in small spaces. The device is available in screw terminal connection and wiring (input / output opposite).
In cases of extreme aggression, DSLP will be in a state of safe end of life: the indication of failure (disconnection) of the surge protector is performed by the extinction of an indicator and switching off the AC (extinction street luminaire) inform the user of the need for maintenance.
Surge protector for use in single-phase TT and TN systems
- DIN rail mounting, very compact (low profile)
- Screw terminal connection
- Status indicator
- Disconnection AC end of life
Basic circuit diagram
|SPD according to EN 61643-11 / IEC 61643-11||type 2 / class II|
|Nominal a.c. voltage Un||230-275 V AC (48/62 Hz)|
|Max. AC operating voltage Uc||320 V AC (48/62 Hz)|
|Nominal discharge current (8/20μs) In||5 kA|
|Maximum discharge current (8/20μs) Imax||10 kA|
|Max. load current IL||5 A|
|Residual current – Leakage current at Uc [IPE]||None|
|Withstand on Combination waveform – Class III test Uoc||10 kV / 5 kA|
|Protection level CM/DM @ In (8/20μs) and @ 6kV (1.2/50μs) UP||1,5 kV|
|Admissible short- circuit current ISCCR||10 kArms|
|Temporatry Over Voltage (TOV) Charasteristics – 5 sec. UT||335 Vac withstand|
|Temporatry Over Voltage (TOV) Charasteristics – 120 min. UT||440 Vac disconnection|
|Failsafe behavior||LED green OFF and AC network cut-off|
|Connection to Network||Screw terminal 1.5 mm2 max.|
|For mounting on||35 mm DIN rail acc. to EN 60715|
|Disconnection indicator||Disconnection and AC line cut-off|
|Remote signaling of disconnection||none|
|Place of installation||indoor installation|
|Degree of protection||IP20|